5 TON Tri Zone Ductless Split Air Conditioner, 60000 BTU 18000 + 18000 + 24000
5 Ton Tri Zone Mini Ductless Split Air Conditioner 60000 BTU. 60,000 BTU Ductless Mini Split AC. 16 SEER Efficiency w/ Heat Pump Technology. With a 60000 BTU total Cooling-Heating Capacity, this Inverter DC mini split. Includes LCD remotes and complete installation kits with 25′ [x3] of piping. 60000 BTU Cooling Capacity. 18k + 18k + 24k. 60000 BTU Heat Pump Capacity. INVERTER DC TECHNOLOGY: 16 SEER. TRI-Zone Setup (3 Air Handlers). Indoor Units – Air Handler. Outdoor Unit – Compressor rated at 60000 BTU’s. Digital, Multi-function LCD Remote Control. Filtration Screens – Multi Folds Evaporator. TRI Air Handlers for Multi-Zone Placement. Washable Filters – Biologically Actv Enzyme. Low Startup Temps – MAXIMUM EFFICIENCY. Pre-charged with freon for 25′ [x3] of piping. Sleep Mode – 24 hour ON/OFF Timer – Memories. Enhanced Copper Coil – Wide Angle Air Spread. 2800 ft² coverage area: 850 + 850 + 1100. Flexible, Quick Installation – Easy Operation. 25 Feet Flared Insulated Copper Tubing. 25 Feet Pipe Insulation. Mounting Brackets for Indoor Unit. Putty to seal piping / holes. Wire Harness Between Indoor & Outdoor. Remote Control w/ Wall Brackets & Batteries. Extend one or two (4) included 25 foot line sets to a total length of 50 feet. WHAT IS DC INVERTER? DC Inverter Air Conditioners are the ultimate cooling and heating technology of the HVAC field. They are called “DC inverter” because the alternative current (AC) is converted to Direct Current (DC) then, direct current inverted back to Alternative current with desired frequency. As known, the current supplied through the wall outlet has fixed frequency which is 60 Hertz. Different frequencies supplied to the compressor will result different running speeds of the compressor. YMGI Inverter control systems use Pulse Amplitude Modulation (PAM) that is the most advanced and energy efficient method of inverting the current. DC Inverter air conditioners bear special compressors that their speed could be changed by increasing or decreasing the frequency of the supplied power. Therefore, unlike conventional split Air Contioners/Heat Pumps which cycle between on and off repeatedly, the DC Inverter control system will monitor the room temperature and adjust the compressor speed automatically. Conventional compressors turn on and off to maintain the room temperature at desired level. This will result compressor to draw tremendous energy each time it starts up. This will also reduce the life-span of the compressor and other components that are turning on and off. Once a conventional system is running, it runs at its maximum speed, consuming the maximum amount of energy in order to produce the maximum of cooling or heating to maintain the desired temperature. The system will then cycle between on and off in an effort to maintain this temperature. When a DC Inverter compressor initially starts up, it runs with a higher speed to bring the room temperature to desired level rapidly. Once the set temperature is reached, it slows down and adjust its capacity to counter the heat loss or heat gain of the building. By this way it will maintain a constant temperature. BASIC OVERVIEW: The indoor unit is hung like a picture frame approximately 6 – 8 feet above the floor usually on an exterior wall. A 2-3 inch hole must be made behind the indoor unit in the exterior wall to run the refrigerant copper tubing, electrical wires and the condensate drain to the outside unit. The indoor unit and outdoor unit are connected to each other by means of refrigerant copper tubing and electrical cables. The condensing unit comes pre-charged with Freon however, the lines still need to be vacuumed to evacuate the excess Nitrogen prior to the final coupling for operation. Although the installation may seem easy to some, certain tools and experience is necessary to complete installation of a mini split See Installation Tip. 5 Year Compressor – 1 Year on all other Parts Registration card will be sent with unit, this card should be completed by an HVAC technician (installer). Installation of a mini split must be completed by a licensed HVAC (Heating, ventilating, & air conditioning) company to ensure any issues encountered in the future are not due to improper installation / workmanship. Even though mini split setup is below the expertise requirements of central AC systems, these are not “plug-n-play” units that can be properly installed without certain tools any prior HVAC – electrical knowledge. The installation includes electrical, gas, and refrigerant connections and generally regulated by a multiple sets of laws, codes and guidelines, at the federal, state and local levels. The failure to properly install HVAC equipment can raise personal safety and performance concerns. If you receive a damaged or defective product, a replacement unit will be sent out Free of cost. SOMEBODY MUST BE ON SITE TO ACCEPT / SIGN FOR Order. Only ships to the lower 48 Contiguous United States. Swap 18k Wall Mount for Ceiling Cassettes. Swap 24k Wall Mount for Ceiling Cassettes. Swap all 3 Wall Mounts for Ceiling Cassettes. Swap 18k Wall Mount for Susp. Swap 24k Wall Mount for Susp. Swap all Wall Mounts for Susp. Customize your system to meet your requirements – see below table for available output options. 12k + 18k + 24k. 18k + 18k + 18k. 12k + 24k + 24k. 9k + 24k + 24k. 18k + 24k + 24k. 9k + 12k + 12k + 24k. 9k + 9k + 18k + 24k. 9k + 12k + 18k + 24k. 9k + 12k + 18k + 18k. 9k + 18k + 18k + 18k. 12k + 12k + 18k + 24k. 12k + 12k + 12k + 24k. 9k + 9k + 24k + 24k. 9K +9K +9K +9K + 12K/18K/24K. 9K + 9K + 9K + 12K + 12K/18K/24K. 9K + 9K + 12K +12K + 12K/18K/24K. 9K + 12K + 12K + 12K + 12K/18K. 12K + 12K + 12K + 12K + 12K/18K. 09K + 09K + 12K + 12K + 18K. 09K + 09K + 12K + 18K + 18K. 09K + 12K + 12K + 18K + 18K. 12K +12K + 12K + 18K + 18K. Air handlers are available in 9k, 12k, 18k and 24k outputs. Be advised, for arrangements where combined output of all heads exceeds rated capacity of condenser (60000 BTU’s) – the total output will not exceed 60000’s when all air handlers are running at full capacity simultaneously. However, overated zones will draw required capacity from other zones either running at lower settings or areas that have reached thermostat settings to obtain rated output. For example, with a 12k-12k-12k-12k- 18k configuration, the total output will be along the lines of 11k-11k-11k-11k-16k when all zones are running on high/full settings at the same time. However, once a zone obtains set temperature and/or operates at a lower setting, the capacity will bleed off into zone that needs the extra push to obtain the 12k-12k-12k-12k-18k yield. View the Mini Split FAQ >. View the Mini Split Outline Diagram >. The item “5 TON Tri Zone Ductless Split Air Conditioner, 60000 BTU 18000 + 18000 + 24000″ is in sale since Sunday, November 03, 2013. This item is in the category “Home & Garden\Home Improvement\Heating, Cooling & Air\Air Conditioners”. The seller is “thermospace_acs” and is located in O’Fallon, Missouri. This item can be shipped to United States.
- Brand: YMGI
- MPN: Sanyo YMGI-T1 Compressor Mini AC Heat Pump, 60,00
- Type: Split System
- Cooling BTU/Hr: 60000
- SEER: 16